UVC Lamps are arranged and installed in front or behind the cooling coil of each AHU (Air Handling Unit). The Lamps are arrayed such as to give maximum irradiance to the cooling coil surface. They are mounted on aluminium frames and are powered remotely from a control box housing the ballasts and sensor boards. This control box is mounted outside the AHU, out of the air stream. This is a customised solution and each AHU requires one control box and an appropriate number of lamps, depending on the size of the AHU.
RydAiR’s Duct Mounted Units (DUV Type) and are designed to be used in confined areas like Fan Coil Units (FCU) or in Air Conditioning Ducts. DUV units provide 360° irradiation. They use high output lamps assembled with a ballast housing assembly that can be easily installed by opening a 50mm hole on the side of the FCU or duct. The housing is attached by means of self-taping screws on the exterior of the duct/FCU. The UVC lamp can be easily removed by opening the housing cover and releasing 4 retaining screws. The ballast is not disturbed during lamp change. DUV units come with an on/off switch with an LED light. Building Management System (BMS) Card for each unit is available as an option.